"Rather than recommend an ERV, how about some thru wall exhaust fan(s) in the bath room(s)? Put them on timers so they don't run all the time.
That kitchen fan REALLY needs to exhaust outside. I would make that a higher priority than the…"
"This looks like a common type of system for Arizona. Most of the time that package unit would be located on the roof and the ducts run down thru the roof. A lot of units installed that way were evap coolers that were replaced with an air…"
"I agree with you so far. But that just means that the vapor barrier is less leaky than the duct. (If the vapor barrier was more leaky than the duct, the vapor barrier wouldn't move.)
But my experience and test data says that…"
"I run into this all the time. You CAN test those ducts. If you want a good quality installation - you should test those ducts and they should meet the leakage specified.. A typical installation leaks 30% of the air thru the…"
"Wrightsoft has an option to include a fireplace in a zone. I would use that option since it complies with the Manual J instructions. If you use some other method (hole or heating source) you should make sure your method complies with…"
"UV lights have their place - but in my opinion are ridiculously oversold. In order to do ANYTHING worthwhile they MUST shine directly on the evaporator coil / drain pan. Any other location and they do nothing useful. Only when the…"
"The fan speed needs to be set to provide the air flow to each room calculated by the Manual J. It was rare to have a contractor do a manual J or adjust the fan speed until recently. The City of Austin (Texas) required thru the energy…"
Welcome to Home Energy Pros! Feel free to join the conversation in the Forum and Groups. And share your energy efficiency photos, videos and upcoming events. If you're blogging about home performance, this is the place for you!
Don't forget to upload your profile photo. And, add your location on our Member Map!