The new concept of "controlling airflow" is discussed with a Savings-to-Investment Ratio (SIR) calculated. Controlling airflow includes 1) air sealing to red...
Tags: 62.2, ASHRAE, Dynamics, Energy, RED, More…Residential, SIR, air, airflow, controlling, infiltration, ratio, savings-to-investment, sealing, ventilation
Join Home Energy Pros
David, I am the guy who put together and narrated the video.I am sorry you missed the section in the video about increased heating load resulting from ventilation, which was 6.4 therms (slide 9). I did mention the increased cooling load, but did not include it in the SIR calculation because of the location; Portland, Maine, where cooling is a minor issue. If you use this analysis in a heating/cooling climate, both the heating and cooling load increases from ventilation should be included in the SIR equation numerator. The RED Calc Free Advanced Infiltration tool reports both heating and cooling loads.
Regarding maintenance, you are correct, I did not include any maintenance costs. If these were included they would be subtracted from the numerator as a recurring annual cost and would lower the SIR value. I ignored these costs because we don't have a good idea of what they are. Of course, there will be some homeowner work involved, such as cleaning the ventilation fan blades, etc. We hope to get a better idea of maintenance costs for ventilation systems within the next five years or so.
It is best practice to add ventilation to each room using ductwork, as you suggest, but it is not required by the ASHRAE 62.2 standard. I assumed a high quality exhaust fan installed in a centrally located bathroom would provide local and whole-building ventilation (this complies with ASHRAE 62.2). If the ventilation system is more complex, the cost of installation would increase. This would, of course, impact the SIR value. A ventilation system that distributes fresh air evenly throughout a home is preferred. However, it is common that this best-practice solution will not fit into the project budget, especially for the folks working within the low-income weatherization program.
You did not add the (other) expected yearly running costs for the ventilation unit (additional air conditioning costs for heat/coll/dehumidify, any replacement parts/service, etc.) in the initial SIR computation; you only talk to the fan electrical costs. Also note: if the structure does not already have duct work (a very common occurrence in older buildings) the additional ventilation duct work costs make this proposal very costly, and assuming a single exhaust fan will provide adequate ventilation to each individual occupied room - especially with closed doors - without dedicated duct work is problematic regardless of what the ASHRAE prescriptions preach. It is the reason why paired supplies/returns are the best way to deliver conditioned air to each occupied room vs. central supplies/returns.
Welcome toHome Energy Pros
Sign Upor Sign In
Or sign in with:
Started by Carly Maltais in HVAC yesterday.
Started by SolyMoly, Inc in General Forum yesterday.
Started by Jim Tenhundfeld in General Forum. Last reply by Brad Cook on Saturday.
Started by CharlieK in General Forum on Thursday.
Started by Diane Chojnowski in General Forum on Thursday.
Added by Barbara Smith
Added by Tom White
January 23, 2017 to January 24, 2017 – Portland Marriott Downtown Waterfront
January 24, 2017 at 9am to January 25, 2017 at 12pm – Bristol Community College at Commonwealth Landing
January 26, 2017 from 1pm to 2:30pm – Eastern Time
February 8, 2017 to February 10, 2017 – San Diego Convention Center
February 9, 2017 from 1pm to 2:30pm – Eastern Time
Welcome to Home Energy Pros – the unique digital community by and for those who work in the home energy performance arena.
Home Energy Pros was founded by the developers of Home Energy Saver Pro (supported by the U.S. Department of Energy) and brought to you in partnership with Home Energy magazine. Home Energy Pros is sponsored by the Better Buildings Residential Network. Please honor our Guidelines
© 2017 Created by Lawrence Berkeley National Laboratory.
Report an Issue |
Terms of Service
Please check your browser settings or contact your system administrator.