# Humidification: Forced-Air Systems

Months fly by, and it is closer to Fall in New England.  Soon most local Plumbing, Heating, and Cooling companies will be consumed with Fall maintenance programs.  I remember spending countless hours a week dealing with humidifiers, whether it was the old Skuttle drum style, the Aprilaire bypass version, or even the steam models that have actually been improved over the years - particularly Honeywell's Truesteam.  The one common theme that always arose was: What do I set the humidistat for?  If you loyal readers remember, a while back I wrote a short blog about ASHRAE's Psychometric Comfort Zone.  Based on this time tested theory, you can set the Relative Humidity (RH) anywhere between 30-60%!  With scorched, or forced-air, systems it is desirable to keep the RH between 35-45% in order to prevent static buildup (ACCA Manual RS).  But, every home is different.  In order to properly sense the RH, most humidistats are located on the return duct.  This may represent the RH at some point in the house, but not everywhere.  So, what is the maximum RH that should be set?  I say it depends on the windows - as visible condensation on the windows can cause many problems.  There is a possibility of concealed condensation in walls, but if a vapor retarder is used and installed correctly, this should not happen in New England.  As a Service Technician, we can only worry about the visible condensation.  If concealed condensation is a concern, please contact a qualified Building Analyst!

 Equation for Surface Temp.

Visible condensation occurs on surfaces that have a temperature below the dew point of the air.  This is why we get "dew" on the grass or my car most summer mornings.  Or why an evaporator actually condensates during operation in our climate.  The temperature of the coil (Evaporator Saturation Temp) is lower than the dew point of the return air.  In order to find out the maximum RH prior to visible condensation, you should use this equation and a Psychrometric chart.  You will need to know the indoor and outdoor design temperatures, and the u-value of the device calculating for.  Since the weak point in most walls is the window, you should find the lowest u-value window in the conditioned space. If you were solving for a wall or ceiling, remember that the U-Value = 1/R-value, or the inverse.

 .49 U-Value Window in MA

For example, lets say your design temperatures were 0F (typical local outdoor) and 70F (2009 IECC and building code compliant indoor), with a window that has a .49 U-Value ( typical double pane, wood frame).  Using the formula, you can determine the temperature of the window at design temperatures, in this case 48F.  This correlates to a dew-point of about 47F.  Then, use of your psychrometric chart (I am sure "there is an app for that") you can determine the max setting for your central humidifier is about 45% RH.

 .36 U-Value Window in MA

Control of this is very important for most new homes as this math with a Low-E window having a .36 U-Value may not yield any visible condensation until the relative humidity hits close to 60%!  If technicians are using the old method of visible condensation, it may be too late for "insert issue here" (concealed condensation, mold, damage to paintings, pianos, etc) or I like to say the many possibilities of IAQ.  In fact, did you know that just as much (if not more) bacteria, viruses, fungi, and mites grow above 60%RH as they do below 30%RH?  (see ASHRAE Systems and Equipment Handbook, 2000) Not only does the static vanish between 35-45%, but so does the rest of the unwanted possibilities.  Ever wonder why condensation builds in attic duct systems and supply registers during the winter?  Check out the duct insulation and do the math...

http://excessair.blogspot.com/2012/09/humidification-forced-air-systems.html

Views: 767

Comment

Join Home Energy Pros

Comment by Robert Riversong on September 23, 2012 at 1:46pm

I would have to differ with you on window surface condensation being a late sign of moisture problems, as it is typically the first sign - it will become visible immediately rather than take weeks or months to develop, such as mold and rot.

The correct formula for inside surface temperature is:

Tsurf = Tin – (Rfilm/Rtotal) x (Tin – Tout)

With:

Tsurf = inside surface temperature

Tin = inside air temperature

Tout = outside air temperature

Rfilm = R-value of inside air film

Rtotal = R-value of entire cross-section (including inside and outside air films)

ASHRAE standard R-values for air films:

inside vertical surface = 0.68

outside vertical surface = 0.17

So your formula is an approximation that ignores the combined 0.85 air film R-value and uses a slightly lower (0.65 instead of 0.68) interior air film value to compensate. But at smaller unit R-values, it becomes increasingly unreliable. With an R-3 window unit, the surface temperature is about 5% low (54.83° instead of 57.64°). With an R-2 window unit, it's almost 13% low (47.25° instead of 53.30°).

Comment by Christopher Morin on September 23, 2012 at 10:12am
Hi Robert! Thanks for reading my blog and providing some valuable insight! I agree, concealed condensation in our climate during the winter months will definitely be caused by internal humidification and exfiltration, requiring air sealing. The problem with this is that normally by the time there is visible surface condensation it is likely too late for inside that wall! Like a lot of poorly controlled "finished" basements in New England.

Unfortunately, I do not know the derivation of the "visible condensation" formula. It was taken from ACCA Manual RS, by P.E. Hank Rutkowski. Almost all of their manuals are ANSI accredited, but I did not see a stamp on this one yet as the latest copywrite is 1997. Are you aware of a more accurate formula? If so, I would please ask you to share so I may compare and possibly ask Hank for a clarification...
Comment by Robert Riversong on September 20, 2012 at 9:38am

Christopher,

Do you know the derivation of that inside surface temp formula? It appears to be a very rough approximation and I wonder where the 0.65 factor comes from.

Also, a correction: In a cold climate, a vapor diffusion retarder has little impact on what you call concealed (or interstitial) condensation. It is almost entirely air exfiltration that causes such envelope condensation problems, by a factor of 9:1.

Comment by Curt Kinder on September 16, 2012 at 6:50pm

Holding indoor humidity between 35% (winter) and 45% (summer) seems to me the holy grail.

## Featured Forum Discussions

### What's the Most Profitable HVAC Job for Your Company?

Started by Wayne Melancon in HVAC. Last reply by Wayne Melancon 11 hours ago.

### Lighting replacement - 300 watt LED flood light

Started by Mary Sinkler in General Forum. Last reply by Jan E. Graveamker yesterday.

### Home Performance is Failing - let's turn that around?

Started by tedkidd in General Forum. Last reply by Nate Adams on Monday.

### Glass Block Windows

Started by Ken Kalke in Best Practices. Last reply by Sean Lintow Sr on Saturday.

### EZ Green Home is Hiring!

Started by Chloe Chapman in General Forum Jan 5.

• View All

## Latest Activity

"Congratulations on your new postion. Looking forward to working with you in the near future. Best…"
5 hours ago
Michael Dunseith joined Kirsten Richnavsky's group

### Retrotec, Inc

5 hours ago
"I'll agree with you there Ken. We'll get shopped by residential when the customer already…"
11 hours ago

### IMG_3138

"and....this was the best looking spot in the air handler. Seal the unit if you want to have any…"
12 hours ago

### IMG_3139

"Beginnings of mold....due in some part to leaks in air handler pulling hot humid air from…"
12 hours ago
Horace Douglas Hunt, Jr. posted photos
12 hours ago
"What is your "Key Performance Indicator" dollar per hour? gross dollar per man day? % of…"
22 hours ago
"Hi Mary, What is the purpose of lighting the backyard ?  Sense of safety, night time…"
yesterday

## Events

• ### Better Buildings Peer Exchange Call: State of the Union: Best Practices from ‘Most Improved’ Energy Efficient States in 2016

January 19, 2017 from 1pm to 2:30pm – Eastern Time

• ### Better Buildings Peer Exchange Call: 0 to 60: Best Practices for Accelerating Program Performance

January 26, 2017 from 1pm to 2:30pm – Eastern Time

## Home Energy Pros

Welcome to Home Energy Pros – the unique digital community by and for those who work in the home energy performance arena.

Home Energy Pros was founded by the developers of Home Energy Saver Pro (supported by the U.S. Department of Energy) and brought to you in partnership with Home Energy magazine.  Home Energy Pros is sponsored by the Better Buildings Residential Network. Please honor our Guidelines