# Duct Gains: Why do we hate R-8?

Ever since the adoption of the 2009 International Residential Energy Conservation Code (IECC), duct sealing efforts have been tested using the total leakage or leakage to outdoors methods.  It really is amazing how much duct gains effect the operation of your equipment and the comfort of your customer.  The missing part of "duct testing" appears to be how well the ducts are insulated.  Sure, you are required to use R-8 insulation on supply ductwork when located outside the building envelope, but how do we know it was installed correctly?  We're not required to test like the duct leakage codes, so is a check in the box sufficient?  How about we use some simple math to figure the gains, or lost capacities in cooling, and hold everyone to a standard - check out the equation below.

Sensible Btu/hr = CFM x Delta T x 1.08
So, based on this math, one can take a few simple temperature measurements and calculate the lost sensible capacities due to duct leakage and insulation.   You should measure the temp of the air entering the return grille and at the unit to figure the return gain in sensible temperature.  I would also recommend averaging the temp readings at the furthest supply register, an average supply register, and a close one to figure the delta T from the air exiting the coil or air handler.  Do the same for an extensive return system.

When you start measuring, it is very scary what you start to find.  As you can see, like the industry accepted national average, this system is losing 30% of the 3-ton capacity through it's well sealed, but poorly insulated duct system.  Unfortunately, the method is not perfect since a hotter day in the attic could cause greater gains.  But, that would be the time to sell duct sealing and insulation to the homeowner!  Any of you energy auditors out there could probably comment on how much attic ducts effect home infiltration as well.  So, why do we hate R-8 insulation?  Is it really just the hassle of wrapping the equivalent of a blanket around the ducts?  I don't recommend retrofitting a distribution system in an attic in the middle of July, but maybe it makes sense to offer to come back in the Fall?  Please, don't just leave it be!  Doing so makes it hard for this tree hugger to sleep at night!

http://excessair.blogspot.com/2012/06/duct-gains-why-do-we-hate-r-8...

Views: 1539

Comment

Join Home Energy Pros

Comment by Bob Blanchette on June 29, 2012 at 6:44pm

The best bet is to reduce duct surface area if you can't get the ductwork into conditioned space. Have fewer registers and larger ductwork instead of lots of registers with small ductwork. Use truck/branch instead of '"ductopus". Keep runs short as possible. Eliminate runs to small/lightly used spaces. Put registers on sidewalls closer to the air handler, set sidewall registers to blow out into room.

The return isn't as big of an offender as the supply. As long as return is tightly sealed the wetbulb temperature won't change much. Wetbulb determines evaporator load. Then there is doing what you can to reduce attic temps, the best solution is typically large area passive vents. If you can see light coming through while in the attic, it's working...

## Featured Forum Discussions

### Strange IR Image

Started by Larry Nissman in General Forum. Last reply by Bryan Gabriel on Tuesday.

### 7,200 Normal Homeowner Minds Blown by Proof Is Possible Tour, Private Market Demanding Proven Home Performance

Started by Corbett Lunsford in Marketing. Last reply by Robert DV Feb 16.

### BPI Supports Strong Consumer Protection in Residential PACE Financing Programs

Started by Quinn Korzeniecki in General Forum Feb 10.

### Hero Pace Program?

Started by Horace Douglas Hunt, Jr. in General Forum. Last reply by Ryan Miller Feb 9.

### BPI February Newsletter & New Logos

Started by Quinn Korzeniecki in General Forum Feb 9.

• View All

## Latest Activity

Jeffery Liang and Ellen Phillips Soroka joined Home Energy Pros
yesterday
Charles Cormany added a discussion to the group Job Board

### Energy Efficiency Incentive Program Manager - Efficiency First California (Berkeley)

Position Title: Program Manager Terms: Full time, available immediatelyAbout Efficiency First…See More
Thursday
Charles Cormany joined Diane Chojnowski's group

### Job Board

This group is for posting jobs related to all aspects of the home performance industry including…See More
Thursday
Thursday
terry nordbye added a discussion to the group Energy Auditing Equipment for Sale, Trade or to Purchase

### Combustion anaylizer Testo 310

This little beauty only has a few hours on it. Almost brand new in box.Sell: \$350.Terry 415 669…See More
Thursday
Barbara Smith's video was featured

### Indiana HCA...On Location - Celebrating 40 Years of the Weatherization Assistance Program (WAP)

The Indiana Housing and Community Development Authority (IHCDA) interviewed two clients of Weatherization Assistance Program (WAP). Both homes were weatheriz...
Thursday
Home Energy Magazine's blog post was featured

### Art Rosenfeld's Legacy

Art…See More
Wednesday
Efficiency First California and Kevin Daly joined Home Energy Pros
Wednesday

## Home Energy Pros

Welcome to Home Energy Pros – the unique digital community by and for those who work in the home energy performance arena.

Home Energy Pros was founded by the developers of Home Energy Saver Pro (supported by the U.S. Department of Energy) and brought to you in partnership with Home Energy magazine.  Home Energy Pros is sponsored by the Better Buildings Residential Network. Please honor our Guidelines