Home Energy Pros
Before BPI Certification, this problem probably would not have been noticed or understood. The home occupants were a 96 year old woman and her elderly & disabled son.
Join Home Energy Pros
At this point, spillage, worst case & draft #'s were a moot issue. It was determined that the interior of the chimney this was venting to had collapsed, so no draft. With no nearby location to exit the structure via standard flue pipe, a decision was made to replace the induced draft natural gas unit with a condensing furnace. If the chimney wasn't blocked, that B-vent flue would have been repaired/replaced to remove the smaller diameter choke point.
Nice catch, right next to a leaky return...
Pass spillage? Worst Case Caz and draft pressure numbers?
Welcome toHome Energy Pros
Sign Upor Sign In
Or sign in with:
Added by Tom White
© 2016 Created by Lawrence Berkeley National Laboratory.
Report an Issue |
Terms of Service
Please check your browser settings or contact your system administrator.