"Target SH = [(3 x indoor wb) - 80 - ambient] / 2 (°F)
Usually, if you are charging an ac , the manufacturer gives you a superheat range they want the equipment to operate at (usually 6-8 degrees) The higher the wetbulb the more…"
"In my opinion you are trying to get very detailed about equipment that is designed to perform in a wide range of climates and environments. Unless a furnace is operating at it design max, it will always be oversized for the load. (Full…"
"There is a pump kit that will install under a sink or in a bathroom. This pump will be activated by a button and it pumps the (colder) water in the Hot water pipe into the cold water pipe. Once it senses heat it will shut off and then…"
"answer ! - It is a dungeon
Answer 2 - it has been placed on part time work so it has lost its incentive to excel.
Answer 3 - There is no sound with out a receiver to hear it, there for YOU are weird for hearing it.
Honestly, These are problems…"
"It looks better on paper than in real life applications. Both Amana and Lennox came out with dual heat applicationa that would heat the home and hot water. Eff ratings on the heating side were about 92-97% and the water heaters were in…"
"Super heat readings without knowing airflow only gives you 1/2 the equation. Dirty filters/ low airflow/refrigerant overcharge/low temp in building or low outdoor temp will all affect the superheat of the system. If the superheat is out…"
"For propane, you can look at the burner orfice size. there are charts that give the btu rating for the orfice size. then multiply by the numbers of burners. will give approx output. LP orfices are usually slightly smaller btu than…"
"There are a number of options - one manufacturer 9LG ductless) makes a square wall unit that can have a picture/art in the front. There are also heads that can be installed in a ceiling ( if you have enough space) so all you see is…"
"I just go through the filter. if it is not metal or electronic. Leave the filter in place and poke a hole with your probe in a corner. If you want to know the pressure drop across the filter place the probe just under the filter…"
"You need more information before you suggest what the appropriate answer to the customers problem would be. Do loads on the house and each floor. Loads tell you equipment sizing which tells you air flow requirements. Now you have…"
"GE and other heat pump water heaters will dehumidify the area they are located in and use the heat gathered to heat the water.
Bob, is right Trane VS systems have the capability to vary fan speed to the humidity and work very well in my…"
"MIni splits work fine as spot cooling/heating and inverter tech is great but has a long way to go to meet loads in Kansas.
Even the manufacturers say their product in not designed to handle whole house loads or conditions. (Meeting last…"
"I agree with what you say. Properly charged units perform better and last longer while using the minimum amount of electricity they can. I will give you a reason why SEER came in. It had little to with improving efficiency by looking at…"