"Linda, I am tempted to say "Don't make other categories". I think that people who try for THC status and fail to make the criteria should still be in the case studies. Their efforts can help in the learning. Did they not meet their…"
Linda Wigington distinguished between deep retrofits & deep energy reductions, thus expanding the range of strategies & tactics from which we might propose when engaging with people, the ones who choose.See More
"That works in Hawaii. Today my rooftop PV modules are under snow. Last week they were under snow. Sometimes they stay covered for 4 months. If they were my hot water system, that would be a long time between showers ...
Here is a report on energy consumption and usage patterns on some Canadian homeowners who switched from storage to tankless. You can see the range of results. There were usually operating savings but those savings might have trouble…"
"I have gotten 6700 PPM CO off a hybrid that had a bad valve. I have seen a 66' mustang 940 HP got 62,000 PPM CO. Flue gas meter go up to 8000 PPM CO, so to get the big number must use very high end testing meter. With Garage door…"
Thanks for those ideas. The garage door hardware on the ceiling could be a problem, and would be a big impediment if the ceiling were to be dropped to access the floor above. Junction boxes would have to be checked.
I was part of the team…"
"Ttwo blower doors? If so does the garage have a separate door to the outside, or only one door into the house?
Measure house with garage door closed (normal conditions), measure house with garage doors open(living…"
"The reason I dislike foam in the garage -- even under a layer of sheetrock, is that owners have the tendencies to puncture the and hang things from the ceiling. I'm not sure the stats, but after the kitchen, I believe garages are…"
"Don, Building Sciences Corp may have paired up with the BuildAmerica program to test. Your work at CMHC, the northern state/province universities. In Washington State - the people at the WSU building/energy efficiency…"
"the very big thing is sealing the return air. When the fan is on and not sealed will suck the car gases in to the building. I seal the return first. To prove the return is sealed I use fog like used in the 70' disco…"
""Avoid the foam"???
VOC's - one should be ventilating that area & they should be gone before anyone regains access
CO - remember the "P" in the GWP piece stands for potential & with the fuzzy math they used... well…"
Thanks for the leads. I was the manager of the CMHC research. I recognize that we have established that garage-to-house air movement exists, and that it often brings in polluted air. What I am looking for now is the practical side of air…"
"Don, I would also do an internet search or ask for queries about indoor air quality, Alaska (or province) and garage. I know this has been studied and researched by a lot of the universities and building science groups. The number…"
"Bud, CMHC tested the flow vs. pressure performance of a Saskatchewan loop back in 1987. The report is likely still around but essentially the looping just reduced the flow rate compared to a straight inlet, by introducing a 180 degree turn. The test…"
"The NPP testing that I did was in the early eighties. We simply measured the cross-wall pressures through any wall orifice or opening we could find, and then graphed the pressure differences against height to find the P=0 intersection. On a calm…"
Welcome to Home Energy Pros! Feel free to join the conversation in the Forum and Groups. And share your energy efficiency photos, videos and upcoming events. If you're blogging about home performance, this is the place for you!
Don't forget to upload your profile photo. And add your location on our Member Map!