Cross-section of frost-protected shallow foundation for 12" truss-wall framing system.
Join Home Energy Pros
I forgot to include the BSC link: http://www.buildingscience.com/documents/insights/bsi-003-concrete-...
The other consideration is the very high global warming potential of XPS, for which a new analysis by Alex Wilson and friends shows becomes worse over its lifetime at more than about R-15-20.
This represents a balance between minimizing heat loss from a radiant slab into the ground and allowing sufficient downward heat loss to maintain the foundation as frost-proof (as well as moderately earth-coupling the house to the ground in the event of prolonged periods without supplemental heat, such as power outages or winter vacations).
Most proponents of superinsulated building would put more than R-10 under the slab, particularly a heated slab, with Passive House folks sometimes using as much as R-40. So I consider 2" XPS a minimum for this application, which includes FPSF, radiant and solar thermal mass slab.
Extruded (of course). I also like the way that you achieve the R15 edge requirement. I have modeled energy loss comparing 2" XPS with 1" XPS in well drained + soils climate zone 6. and have reservations about the added cost of 2" under the slab. Knowing that you only get 1 shot at getting this right, I wonder what you thoughts are and where you would draw the line between 1" & 2".
Can you offer a link to the Building Science Corp reference?
Yes, that should have been noted in the section. I use a Tu-Tuf 4 mil laminated vapor barrier that is designed for sub-slab applications and is highly tear-resistant. All seams are taped, as well as all seams of the XPS (not EPS) insulation board.
It is a bad idea to put any "reservoir" layer of sand between the vapor barrier and the slab - Building Science Corp addresses this - as it is likely to create moisture problems. The slab finisher loves it because he can power trowel the slab and get home to his Budweiser sooner, but a vapor barrier does not cause slab cracking or curling.
Do you have a moisture barrier below the slabs' EPS? I have found that a 1" layer of sand, placed over the EPS helped to protect both the insulation and vapor barrier. This may have also provided some amount of moisture control during the curing phase. I have had concrete contractors exclaim that slabs poured over EPS are very prone to cracking because of the way the the moisture escapes form the curing slab.
I have not had these cracking issues, on the radiant heated slabs that I have done over the past 30 years, but I have seen them in slabs that did not have proper edge insulation.
Welcome toHome Energy Pros
Sign Upor Sign In
Or sign in with:
Started by Kim Tanner in General Forum. Last reply by Eric Kjelshus on Thursday.
Started by Joe Clark in General Forum Aug 11.
Started by Barry L NewDelman in General Forum. Last reply by Daniel Cullen Aug 10.
Started by Brandon Walton in General Forum. Last reply by Iain Walker Aug 10.
Started by Mark Thomas in General Forum. Last reply by tedkidd Aug 3.
© 2017 Created by Lawrence Berkeley National Laboratory.
Report an Issue |
Terms of Service
Please check your browser settings or contact your system administrator.