Leaky recessed-can lights were big energy wasters before they were sealed.
Tags: air, audit, energy, leaks, lights, More…recessed-can, retrofit, savings
Albums: Energy Audit at 10 Maple Lane
Location: Walnut Creek, California
Join Home Energy Pros
Sealing up a can light with a foam board box is a code violation and unsafe. If you do it, you need to use a non combustible material, like drywall, or one of the tenmat mineral wood recessed light covers. http://www.tenmat-us.com/
The Cree LR6 LED conversion kits are nice, and should cut down on air leakage. However if you install them in a non-IC rated can light housing, you still are not supposed to put insulation over the top of them. So you would still have to baffle around the can in the attic. The best option for Non-IC can lights is to remove them and replace them with IC rated fixtures, or some other alternative lighting.
Haven't heard of that Bob, thanks for the heads up!
Sorry, that was five years ago when Larry wrote his article.
Larry Armanda, who used to call himself the "Can Man" because he spent a lot of time looking at and fixing recessed can light leaks, wrote about it for Home Energy in 2005 "Further Wrestling with Recessed-Can Lights" (Sept/Oct). He didn't find a great retrofit kit, but Builders Best and Lithonia Lighting put out some good kits for sealing the can lights. That was ten years ago, so things may have changed.
At our house the contractors used a non-expanding spray foam to seal the lights where the fixture meets the ceiling. (The retrofit kits have a spongy gasket that does the same thing.) Then our contractor made boxes out of foam board to insulate the can-lights on the attic side. There was one problem—the can lights with incandescent lights stay on for about two hours and then the thermal cut off switch turns them off. The insulation makes the light fixture heat up rapidly inside. Without a thermal cutoff switch, the fire danger would be pretty serious. We put CFLs in the can-lights and fixed that problem. We need a brighter light in one room, over a desk, and still have an incandescent there. It cuts off after a few hours and I take it as a signal to get away from my desk for a while! They should be CFLs that give that kind of light but we haven't found it yet.
Hope this helps!
Do you know of a good kit for converting the leaky lights to sealed ones? I pulled my leaky lights out of my house and replaced them with sealed lights but only because I was able to access them via the attic space.
Welcome toHome Energy Pros
Sign Upor Sign In
Or sign in with:
Started by Larry Nissman in General Forum. Last reply by Bryan Gabriel on Tuesday.
Started by Corbett Lunsford in Marketing. Last reply by Robert DV Feb 16.
Started by Quinn Korzeniecki in General Forum Feb 10.
Started by Horace Douglas Hunt, Jr. in General Forum. Last reply by Ryan Miller Feb 9.
Started by Quinn Korzeniecki in General Forum Feb 9.
Added by Barbara Smith
Added by Tom White
February 22, 2017 to February 24, 2017 – Chicago Hilton & Towers
March 7, 2017 to March 8, 2017 – Lexington, KY
March 19, 2017 to March 22, 2017 – Nashville, TN
March 20, 2017 to March 22, 2017 – Nashville, TN
April 2, 2017 to April 4, 2017 – Arlington, VA
Welcome to Home Energy Pros – the unique digital community by and for those who work in the home energy performance arena.
Home Energy Pros was founded by the developers of Home Energy Saver Pro (supported by the U.S. Department of Energy) and brought to you in partnership with Home Energy magazine. Home Energy Pros is sponsored by the Better Buildings Residential Network. Please honor our Guidelines
© 2017 Created by Lawrence Berkeley National Laboratory.
Report an Issue |
Terms of Service
Please check your browser settings or contact your system administrator.