Return ducts used floor/ceiling joist and balloon frame wall cavities for return air. Once the walls were insulated the furnace suffocated and pulled all return air from the basement. The worst case CAZ was -12.3pa causing the furnace to backdraft and the basement to reach 97ppm of CO.
You can share this photo in two ways…
Share this link:
Send it with your computer's email program: Email this