# Target superheat formula

You said take wet bulb at unit not in the house am i right or did i miss understand the formula

Views: 4880

### Replies to This Discussion

You take the Indoor Wet Bulb and the Outdoor Temp

Thank You
Can you explain this superheat formula like way do we times it by 3 and mines 80 and mines cond enterning ambient,.

Thanks Mike O

Target SH = [(3 x indoor wb) - 80 - ambient] / 2 (°F)

Usually, if you are charging an ac , the manufacturer gives you a superheat range they want the equipment to operate at  (usually 6-8 degrees)   The higher the wetbulb the more capacity/cooling will be diverted to removing moisture/humidity.

The super heat will show if the TXV is operating correctly as well.  It is a great tool for diagnosis.  If you are an HVAC dealer, your equipment manufacturer rep will be happy to explain it all to you.

All the various scenarios are to involved to train someone here.

Yikes -- Folks help me out. I am confused. As I recall, the target superheat for a fixed metering device (orifice/non-TXV) is dependent on the return plenum wet bulb (at the plenum, not in the house because what the air conditioner sees is what is in the return plenum, not necessarily the same as the wet bulb in the house) and the condenser air entering temperature.

I checked the formula given against the generic table (originally Carrier) and found the formula proposed is way off (not usable). I gets vastly the wrong answer under many scenarios. For example at 58 return plenum WB and 80 condenser air entering temperature it gives a target superheat of 34F, while the standard table gives a target of less than 5F.

Check out the linked table below from the California Title 24 Standards

On the other hand a TXV is a constant superheat valve -- so it should not change with different return plenum or outdoor conditions. For adjustable TXVs some experienced people (like Rick Chitwood) adjust it to 6 degrees F system superheat (system superheat is based on the temperature of the suction line as it enters the outdoor unit on split systems). For a TXV or EXV it is often not adjustable, but you should suspect a problem if it is high (approx15 F or above) or low (less than 3F).

Attachments:

## Discussion Forum

### HVAC integration – the past, the present, and the future

Started by Igor Mitbarg. Last reply by Lucifer Prescott Apr 11.

### Efficient furnace with maximum temperature

Started by Thaara Mar 30, 2016.

### Zehnder North America seeks qualified QA agents

Started by Gary Baggett Mar 4, 2016.

### Target superheat formula

Started by Miguel Orduno. Last reply by John Proctor Feb 18, 2015.

### Now for Something Different

Started by John Porterfield. Last reply by John Porterfield Jan 12, 2015.

326 members

149 members

330 members

190 members

126 members

## Latest Activity

Lee Morris joined Norm Bourassa's group

### Multifamily Buildings

For too long there has been relatively little EE focus on multifamily, but some new programs have…See More
36 seconds ago
Lee Morris joined Sean Lintow Sr's group

### Best Practices (Residential)

Best Building, Retrofitting, or even Auditing Practices - what are they, what should change, what…See More
49 seconds ago
Lee Morris joined Michael Stuart's group

### INFRARED THERMOGRAPHY USERS

This group is dedicated to knowledge sharing and discussion of infrared thermography for building…See More
1 minute ago
Ted Cushman, David H, Suzanne Harmelink and 11 more joined Home Energy Pros
8 minutes ago
Home Performance Coalition posted a blog post

### Home Performance Coalition Announces the Merger of the Home Performance Forum and Home Energy Pros to Become the Premier Sharing Space for Home Energy Professionals

September 26, 2017 - Washington D.C. Creating a collaborative online community for home energy…See More
12 minutes ago
Building Performance Institute posted a discussion

### Siemen Scholarship for BPI Certification - Applications due 11/30/17

The Jon Siemen Memorial Scholarship is intended to help individuals in the industry who are working…See More
44 minutes ago
"Hi Radhika, We just announced today that the Home Performance Coalition is taking over Home Energy…"
1 hour ago
"We just announced today that the Home Performance Coalition is taking over Home Energy Pros. Your…"
1 hour ago