I have proposed spray foam for my clients soffits after showing him the blue region with my infrared camera. The client wants additional return on investment calculations for this measure. I have indicated that this is beyond the modeling capabilities of our software. Any ideas on how to relay the value of this procedure.
Why do you want to insulate the soffits ? What do you see as a benefit ?
If I am reading this question correctly the answer would be 0 - now if you are talking about the area above the top plate up to the roof sheathing & you are going with a hot roof system - that is easily calculated in Rem-Rate or Rem-Design
Thank you for the replies. I should have been clearer. You know that 1/4" gap area when the wall top plate shrinks and air dumps in behind the drywall. I am speaking of the wall- ceiling juncture at the exterior walls where the underside of the roof deck is minimum when close to the eave.
The home has both cathedral trusses and regular gable trusses. Some of the treatment can be done from the attic and some will have to be done by removing the exterior soffit.
The area in question is often a complex of framing details and as you stated, they change with time. Shrinkage, warping and hidden details behind that soffit can create energy loss that shows up dramatically with an IR image. Putting an actual number on what you see in a particular home would be strictly an educated guess. The estimated average r-value over an estimated area can be made to sound accurate, but is strictly a guess. However, guessing at some numbers and calculating the potential extra loss does give you a basis for potential savings that can then be compared to estimated costs. My guess would be a lot of work with minimal payback, all dependent upon each house. If you were foaming other areas already and had that area exposed, then it might work.
As an example I just estimated a 1,500 sq ft ranch, r-40 ceiling, r-20 walls, compromised 6" of ceiling and 6" of walls to r-6 and with my 7,000 HDD and $3.5 oil I would save $120 per year if the compromised area was increased to wall and ceiling values. REALLY rough estimate, but easy to do since I calculate things like this manually.
Sounds like a lot of work for a little reduction in air infiltration. If it could be incorporated with other work in the same area then it would make some sense. Sometimes chasing little leaks can't be justified.
Unless the IR images show large areas of infiltration then some return on investment calculations could be made.
People pay to remove pain. What is the pain?
What is the problem you are curing? If it is simply energy reduction don't be surprised people want payback. I'm not walking 2 blocks for a penny, but I will run to the street for a dollar.
You need to pry open additional problems, particularly if you can't quantify savings.
Ice dams? Icicles? Comfort issues? Remember, high in stack leakage means low in stack coldness. Are there comfort issue low in this house?
Did you get a blower door number?
Answers don't jump out. Realizing that the thermal imaging is from blue to red in just 12 deg of difference means that the top plates are colder but most likely not a real big energy suck. The blower door was 1.5 times BAS so not to bad. The work might not be worth the cost or effort. .
It has been proven that foaming interior and exterior top plates has significantly reduced air infiltration . I include this cost in my heated air infiltration reduction measurement with a list of other items I'll be doing.
Fully agreed &/or I list it as required work for adding attic insulation, etc...
Matthew, etc... while everyone likes to quantify that this has this or that payback or ROI, lets not forget the one basic - the whole house is a system & just cherry picking doesn't do anyone any good and can cost them & you in the long term.