Estimating E savings from air sealing in huge leaky house

I'm asked to estimate the heating energy savings from air sealing a 10,000 sf house built in 1900. The former mansion has 6 undampered chimneys and about 40 windows needing repair as well as doors, some needing replacement and all needing weatherstripping. The house has a semi heated basement, and three stories on top of it.

The house has new radiators in all rooms and a 92% efficient boiler.

How do I estimate the potential heating savings from all the air sealing possible here?

George Matthews

Views: 119

Replies to This Discussion

"A Journey of a Thousand Miles starts with a single step."

Try breaking the house into smaller pieces and working on the "knowns" first.

The most accurate way would be to have a blower door test conducted.  Once you know how much infiltration you have you should be able to determine the total energy waste associated with that air infiltration.

The Retrotec blower door manual has this chart for estimating the energy wasted due to air leakage. This should help you.

David,

Thanks! That is exactly the information I needed to make sense of the blower door data.

Now I need to learn how to estimate the potential energy savings from changing out a 23 y.o. boiler that was 80% efficient when new. The replacement would be a 95% boiler potentially coupled with solar hot water. There are 25 people here who take showers daily.

Also, I've read about heat exchangers to recapture waste heat from the pipes running from showers. "EcoDrain" is one such unit. Does anyone have experience with these? And if so what type of efficiencies are they finding?

George,

If you know the annual fuel heating energy bill you can make an estimate. If you know the cost per therm of natural gas or per gallon of fuel oil you can estimate the total amount of energy required.  For example, for a 80% efficient propane unit and if we assume 340 gallons of propane for heating...
340 * 91,300 * 0.8 = 24.8 MMBTU produced.  We then divide this by 0.95 and 91300 for the new boiler to get 286 gallons required for the new furnace. (91300 is the # of BTU's in 1 gal of propane).  I hope you see my logic...  Or just divide .8 by .95 to get the ratio of new energy required (84%), 16% less energy.

Home Energy Pros

Home Energy Pros was founded by the developers of Home Energy Saver Pro (sponsored by the U.S. Department of Energy, under the American Recovery and Reinvestment Act) and brought to you in partnership with Home Energy magazine.

Latest Activity

Johnny Ritzo posted a discussion

Selecting a Water Heater

I am looking at updating the heating and water heating systems in a rental home I recently…See More
1 hour ago
"When I am asked to fix this home.   I start with a Heat Loss and gain, blower door IR  sq…"
3 hours ago

Edward Foskey just added their location.(via Member Map)

8 hours ago
Martin Easley and Richard Vito joined Home Energy Pros
12 hours ago
"This is a topic I have discussed many times, but unfortunately cost is all too often the deciding…"
16 hours ago
"If you can't talk them into replacing with IC rated... Look into Tenmat - those are designed…"
16 hours ago
Bachi Brunato posted a discussion

Boxing and Insulating Around Non-ICAT Cans

I have a client with 16) 4" halogen recessed light fixtures in the attic.I'd like to cover the cans…See More
22 hours ago
"Could you have them make a simple two line graph of the outside temperature, noting sun/clouds,…"
yesterday
"You make some valid points, especially with the base rate charges. Increasing the base rate instead…"
yesterday
"Amen, make energy show it's true cost instead of subsidizing it. We have some of the lowest…"
yesterday
"The press report really doesn't give enough information to clearly answer why  they are…"
yesterday
"Gustavo, Thanks for the input. I agree with you in that I will be waiting till my system's…"
Saturday

© 2013   Created by Lawrence Berkeley National Laboratory.