# Estimating E savings from air sealing in huge leaky house

I'm asked to estimate the heating energy savings from air sealing a 10,000 sf house built in 1900. The former mansion has 6 undampered chimneys and about 40 windows needing repair as well as doors, some needing replacement and all needing weatherstripping. The house has a semi heated basement, and three stories on top of it.

The house has new radiators in all rooms and a 92% efficient boiler.

How do I estimate the potential heating savings from all the air sealing possible here?

George Matthews

Views: 339

### Replies to This Discussion

"A Journey of a Thousand Miles starts with a single step."

Try breaking the house into smaller pieces and working on the "knowns" first.

The most accurate way would be to have a blower door test conducted.  Once you know how much infiltration you have you should be able to determine the total energy waste associated with that air infiltration.

The Retrotec blower door manual has this chart for estimating the energy wasted due to air leakage. This should help you.

David,

Thanks! That is exactly the information I needed to make sense of the blower door data.

Now I need to learn how to estimate the potential energy savings from changing out a 23 y.o. boiler that was 80% efficient when new. The replacement would be a 95% boiler potentially coupled with solar hot water. There are 25 people here who take showers daily.

Also, I've read about heat exchangers to recapture waste heat from the pipes running from showers. "EcoDrain" is one such unit. Does anyone have experience with these? And if so what type of efficiencies are they finding?

George,

If you know the annual fuel heating energy bill you can make an estimate. If you know the cost per therm of natural gas or per gallon of fuel oil you can estimate the total amount of energy required.  For example, for a 80% efficient propane unit and if we assume 340 gallons of propane for heating...
340 * 91,300 * 0.8 = 24.8 MMBTU produced.  We then divide this by 0.95 and 91300 for the new boiler to get 286 gallons required for the new furnace. (91300 is the # of BTU's in 1 gal of propane).  I hope you see my logic...  Or just divide .8 by .95 to get the ratio of new energy required (84%), 16% less energy.

## Forum Discussions

### Origin of guarded blower door testing

Started by Kim Tanner in General Forum. Last reply by Chris Clay on Monday.

### Managing energy costs quotes

Started by Joe Clark in General Forum on Friday.

### Electro Magnetic Fields (EMF)

Started by Barry L NewDelman in General Forum. Last reply by Daniel Cullen Aug 10.

### When is it too windy to use blower door?

Started by Brandon Walton in General Forum. Last reply by Iain Walker Aug 10.

### Performing home energy audits in Rhode Island

Started by Mark Thomas in General Forum. Last reply by tedkidd Aug 3.

124 members

140 members

300 members

324 members

69 members

## Latest Activity

Home Energy Magazine posted a video

### Marc Rosenbaum, Principal, Energysmiths, compulsive measurer

Home Energy Magazine's series "Legends of Home Performance". "Making a great building involves so many aspects of human experience...it's really about how th...
10 hours ago
Home Energy Magazine posted a blog post

### Women in Building Performance: Julie Michals

Julie Michals is the…See More
10 hours ago
Steve Baker, Valerie Beichner, Dave Jones and 1 more joined Home Energy Pros
15 hours ago
Home Energy Magazine's video was featured

### Testing HVAC Grilles with a Blower Door

Watch home performance testing guru Corbett Lunsford test the pressure, airflow, and velocity performance of some beautiful custom carved wooden return grill...
16 hours ago