# Calculating BTU lost per cfm leaks

Hi everyone,

A couple of my colleagues were discussing the benefits of air sealing, when I was asked if I could quantify the actual value of air sealing based on how many BTU's per CFM(50) of air leak.  The software does the energy savings calculations of air sealing for my clients, but I was never asked the actual value per BTU. I guess if I could answer that I would have a better understanding of the math behind the savings.

Can anyone help me with this? Is there a formula?

Thanks

Luis

Tags: CFM, air, energy, saving, sealing

Views: 866

### Replies to This Discussion

Bud,

"In an article from one of the developers of the "n" number he stated the resulting estimate could be off by minus 50% to plus 100% so calling it a ball park estimate may be generous."

Do you recall the article you found this in?

Thanks,

Graham

I have looked but found no reference to that article.  But my background in research saw those numbers and concluded it wasn't much better than a wild guess, or the old empirical divide by twenty,  But since the results bracket the "20" pretty much, in general they are ok.  Part of what we do is to recognize what fits the many assumptions and what doesn't.  Unfortunately, that might improve our accuracy. but reduce our consistency and it is consistency that our system really demands, even if our numbers are wrong.

Consistently relying on software to generate our answers can be a risky way to do business.

Bud

If you were using TECTITE from The Energy Conservatory, you have this value right away.

Asking for an 'actual value of air sealing' is a research project.

Blower Door guided air-sealing works well for those of us in the real world.

Give the Advanced Infiltration tool a try from Residential Energy Dynamics (RED); I think it will do all you need. It is based on the Alberta Infiltration Model (AIM-2) and it includes TMY3 weather data for North America. It will give you the fuel use (therms, kwh, etc) for infiltration. Start with the pre-weatherization CFM50 and then the post-weatherization CFM50 to determine the savings from air sealing. The tools also does many other useful things.

As a matter of disclosure, I am the author of this procedure, along with my business partner, Charlie Holly.

Bob,

Where does the value 1.08 come from?  I am more familiar with the  "0.018 BTUs per cubic foot to raise its temperature 1° F" that Bud cited.  Using a hypothetical 125 CFM nat. with a delta T of 50 F and your equation I get 6750 BTU/hr.  If I use 0.018 and the same equation I get 113 BTU/hr. Markedly different results.

There is a factor of 60 difference between the answers that Graham is pointing out.

Reply by Graham Irwin 2 hours ago

Remember to convert CFM (cubic feet per MINUTE) to cubic feet per HOUR (i.e. ft3/hr = CFM/60) if you want an answer in BTU/hr."

Bud

1.08 represents the sensible heat constant. Any time that I've done these calcs it was left out because the complexity was beyond the scope of what I was trying to accomplish, but if someone with the time and expertise wants to expound on this I'd like to know more as well.

I'll just turn Bob's equation around:

Q (BTU loss/gain) = 1.08 x CFM (natural) x ▲T (F°)

The short explanation is, we need to convert CFM to hours as Graham posted. Multiply by 60 min/hr

Then we have to specify the thermal capacity of air: 0.018 btus/ft³/F°

When that all gets factored in we get (60 x 0.018) which equals the 1.08 and the units of the equation come out in btus/hr.

I scratched that all out, but typing it in is a pain, so you got the short version.

Bud

Bud,

You explained it just fine.  Makes sense.

Yes, and when I cannot sleep I do my own version counting the length of time my FAN runs to reset my internal temp then take into account the current Delta T of the night and then, finally when does the furnace come back on!

I obviously need help

Don't put any faith in standard formulas that convert cfm50 reductions into air sealing savings.  A house doesn't naturally experience air exchange at a 50 pascal pressure difference.  A blower door will cause air to enter the house from every penetration indiscriminately.  Under natural conditions, air exchange is caused from mechanical ventilation, wind and the stack effect.  An installer who cuts CFM50 in half by sealing windward and ceiling leaks will create MUCH more savings than another installer who just spray foams the sill box.

If anyone is aware of a formula that requires sealing location data to estimate savings, please let me know.  Until then, this is huge opportunity for building scientists to advance our industry.

Dmitri Martin

## Home Energy Pros

Home Energy Pros was founded by the developers of Home Energy Saver Pro (sponsored by the U.S. Department of Energy,) and brought to you in partnership with Home Energy magazine.

## Latest Activity

"Thanks Sandra. We look forward to that, too! "
5 minutes ago
David Eggleton joined Kathleen O'Brien's group

Non-profit specifically aimed at building leadership capacity in those called to create a…See More
33 minutes ago
Tom White posted a video

### Passive House Revolution - Film Trailer

Looking for energy-efficiency in buildings? There's no need to wait for new technology - Passive House buildings use 80-90% less heating and cooling energy—a...
9 hours ago
Patrick Michaelyan's discussion was featured

### Rigid Foam (Polyiso) as a Weather-Resistive Barrier

Hello pros!I have done much reading on the subject and am still in need of a final round of…See More
9 hours ago
Mike Rogers's discussion was featured

### Where do you fall in the "staged" versus "gotta be all at once" discussion?

In several industry conversations over the past few months, there’s been debate about whether we…See More
9 hours ago
Bud Poll's discussion was featured

### I say to-may-toes and you say to-mah-toes

I like that song but I'm showing my age.We often talk about the general public's need to be…See More
9 hours ago
Ethan Bodnaruk's discussion was featured

### Insulating with *Updated* (an oxymoron, right!) knob and tube wiring

Hi everyone,I live in New York State and haven't been able to find good information on whether or…See More
9 hours ago
Craig McManus's discussion was featured

### How to keep mice, critters from getting into duct insulation that is under a house that is on piers.

How do you keep mice, critters from getting into duct insulation that is under a house that is on…See More
9 hours ago
Anthony J Passannante's discussion was featured

### Field Testing of R values

Is there equipment available or testing methodology for calculating the R values of walls and…See More
9 hours ago
David Byrnes's blog post was featured

### What Is the X-Factor In Hiring In Home Performance

An article published in the NY Times, titled, "How To Get A Job At Google" got me thinking about…See More
9 hours ago
Cameron Millard's blog post was featured

### 90% AFUE Wall Mount Furnace

I run an energy program in the mountains of Colorado. We have a lot of homes without existing duct…See More
9 hours ago
Stephanie@SaveOnEnergy's blog post was featured

### New Boston Homes Generate More Energy Than They Consume

In 2013, Boston earned the title of the most energy-efficient city in the United States from the…See More
9 hours ago

© 2014   Created by Lawrence Berkeley National Laboratory.